The S-OC-012-D000 is a recessed, ceiling mounted Occupancy Sensor with Passive Infrared Sensor. The sensor will automatically turn on luminaires to the set dimming level when motion is detected and turn lights automatically after the area is vacated.
The S-OC-012-D000 uses digital PIR Motion Detector Architecture and Dual Element passive infrared (PIR) technology for improved detection coverage for ceiling mount, high bay, and low bay applications. The S-OC-012-D000 is a Class 2 Device designed to satisfy new CA Title 24 requirements for bi-level dimming of lighting fixtures. The sensor is capable of dimming lighting loads down to 0%*, 10%, 25%, or 50%. The sensor is suitable for a variety of indoor applications. It supports ceiling mounts up to 40ft high. Both sensor and power pack are rated for use in temperatures ranging from 22°F to 158°F (-30° to 70°C) and relative humidity from 90 to 95% at 86° (30°C.) *for dim to off, Power Pack or LED dimming driver capable of dimming to off is required.
|Sensor Type||PIR Occupancy Sensor|
|Input Voltage | Current Consumption||12-24VDC | 50mA Sensor|
|Mounting Height||10ft (3m)|
|Max Detection Area* (see spec sheet for details)||20ft Diameter (6m)|
|Operating Temperature||22°F to 158°F (-30°C to 70°C)|
|Storage Temperature||-40°F to 176°F (-40°C to 80°C)|
|Relative Humidity||Relative Humidity|
|Mounting||Recessed in Ceiling|
|Dimensions||2.68” diameter (68 mm)|
End users can program length of time delays, light level sensitivity, sensor range and other settings using the BubblyNet App. Bi-level Dimming ** When motion is detected the sensor will bring lighting up to 100% lumen output. When no motion is detected for the length of TD1, the sensor will send a signal to dim lighting to a specific level set by the end-user. If no motion is detected for the length of TD2, the sensor will send a signal to shut off the light. **The sensor will dim the light if motion is not detected for the first time delay (TD1) and shut off the light if motion is not detected for the second time delay (TD2.) TD2 will only count down after TD1 has expired and the light has dimmed. If motion is detected during TD2, the light will return to full output, and TD1 will restart. If using a power pack, the sensor will tell the power pack to shut off the driver after TD2 expires to turn off the light. If using a dimming driver without a power pack, the sensor will try to dim down to 0% upon expiration of TD2. The S-OC-012-D000 needs to be installed within 30 feet of the closest device within the Bluetooth Mesh network. 12-24VDC power needs to be supplied to the sensor, either with one AC/DC transformer or with the auxiliary 12V output of the driver.